E-mail Us: [email protected]
Shell boilers may be defined as those boilers in which the heat transfer surfaces are all contained within a steel shell. Shell boilers may also be referred to as 'fire tube' or 'smoke tube' boilers because the products of combustion pass through the boiler tubes, which in turn transfer heat to the surrounding boiler water.
Fire tube boilers usually consist of a single furnace tube and a burner. Hence, the control systems meant for heating purpose inside these boilers is kept very simple. Due to their comparatively low operating pressures, the accessories needed to support fire tube boiler systems can be obtained at very economical rates.
Cochran boiler is a vertical, coal or oil fired, fire-tube boiler. It is the modification of a simple vertical boiler with increase in surface area. Cochran boiler consists of a cylindrical shell with its top in a spherical shape. The furnace of the Cochran boiler is in hemispherical shape. The grate is placed at the bottom of the furnace and
then pumped to the boiler by the feed water pump. Fig. 1 A typical smoke tube package boiler 1. Furnace Tube 9. Crown Valve 17. Burner 2. Tubes (2nd pass) 10. Feed Check valve 18. F. D. Fan 3. Tubes (3rd pass) 11. Level controls
Fire tube boilers, also known as smoke tube boilers, are the most common type of industrial boiler employed today. Compared to water tube boilers, they are much more suitable for smaller plant applications because they can better cope with sudden high demand steam fluctuations. Combustion occurs within a furnace with the exhaust gasses ( flue
2021/9/18 · A fire-tube boiler is a type of boiler in which hot gases from the fire pass through one or more tubes within the boiler. It is one of the two major types of boilers, the other being the water-tube boiler. A fire tube boiler can be either horizontal or vertical. A fire-tube boiler is sometimes called a "smoke-tube boiler" or "shell boiler" or
2017/10/17 · Fire-tube Boiler System | Fire tube Boiler working animation video | Fire tube Boiler principle-------------------------------------------------------------
2015/1/4 · Water Tube Boiler Animation: Water tube boiler is a form of boiler where steam is generated by circulating water with tubes exposed to the source of heat. Generally water tube boiler works with steam and the tubes carry hot gases through the water. Main working function of water tube boiler designs are listed in this article.
) Boiler water should be tested and chemically treated according to manufacturer's schedule or on the advice of an Appointed Examiner. This will avoid corrosion and scale formation on heating surfaces. Wastage of furnace, fire tubes or boiler shell can develop10.
Boiler: Definition, Types, Applications, Necessity, and Fuel Used [PDF]
Oil Fired Boilers And Gas Fired Boilers are the basic 3 pass internal furnace smoke tube type design in which flue gases are inside the tubes while water is outside the tubes in the shell. The combustion of oil and gas in a furnace requires atomization of the fuel. Since the fuel entering the burner in bulk amount is either in liquid or gas
Fire tubes boilers are also known as a smoke tube boiler. Water-tube boiler: Water-tube boilers are those boilers in which water flows through a number of tubes (called water tubes) and the hot gases produced by the combustion of fuel in the boiler furnace while on their way to chimney pass surrounding the tubes.
Thermodyne Boilers is supplier of WHRB boiler with Low Cost & High Quality. WHRB is popular Industrial Steam Boiler in India. 3 Pass Wet Back /Dry Boiler Buy Intech model- 3 Pass Internal Furnace Packaged Boiler. It is a conventional 3 pass smoke-tube
The following disadvantages of fire tube boiler are: The fluctuation of load cannot be easily handled. The rate of steam generation is low. A Fire boiler is used in small power plants. The maximum working pressure is up to 20 bar which is a less comparatively water tube boiler. Overall efficiency is up to 75% only.
Combitherm boiler or is known among others as Combi boiler is a unique water cum smoke tube type design. It is the combination of both Water Tube Boiler and Smoke Tube Boiler where some tubes form the enclosed part of the external furnace in which water flows and rest of the tubes are placed in a shell in which flue gases flow.
One or more large cylindrical furnaces are in the lower part of the boiler shell. Above this is a large number of small-diameter fire-tubes. Gases and smoke from the furnace pass to the back of the boiler, then return through the small tubes and up and out of the chimney.
Cochran Boiler: A Cochran boiler is one of the best popular types of vertical multi-tubular, fire- tube boiler. The Cochran boiler is made in sizes upto 2.75 metre diameter and 5.8 metre height. It has a maximum evaporative capacity of 3640 kg of steam per hour, from cold feed, when burning 568 kg of coal per hour.